Direct combustion is the best established and most commonly used technology for converting biomass to heat. During combustion, biomass fuel is burnt in excess air to produce heat. The first stage of combustion involves the evolution of combustible vapours from the biomass, which burn as flames. The residual material, in the form of charcoal, is burnt in a forced air supply to give more heat. The hot combustion gases are sometimes used directly for product drying, but more usually they are passed through a heat exchanger to produce hot air, hot water or steam.
The combustion efficiency depends primarily on good contact between the oxygen in the air and the biomass fuel. The main products of efficient biomass combustion are carbon dioxide and water vapor, however tars, smoke and alkaline ash particles are also emitted. Minimization of these emissions and accommodation of their possible effects are important concerns in the design of environmentally acceptable biomass combustion systems.
Biomass combustion systems, based on a range of furnace designs, can be very efficient at producing hot gases, hot air, hot water or steam, typically recovering 65-90% of the energy contained in the fuel. Lower efficiencies are generally associated with wetter fuels. To cope with a diversity of fuel characteristics and combustion requirements, a number of designs of combustion furnaces or combustors are routinely utilized around the world
Biomass is fed into the combustion zone from underneath a firing grate. These stoker designs are only suitable for small scale systems up to a nominal boiler capacity of 6 MWth and for biomass fuels with low ash content, such as wood chips and sawdust. High ash content fuels such as bark, straw and cereals need more efficient ash removal systems.
Sintered or molten ash particles covering the upper surface of the fuel bed can cause problems in underfeed stokers due to unstable combustion conditions when the fuel and the air are breaking through the ash covered surface.
The most common type of biomass boiler is based on a grate to support a bed of fuel and to mix a controlled amount of combustion air, which often enters from beneath the grate. Biomass fuel is added at one end of the grate and is burned in a fuel bed which moves progressively down the grate, either via gravity or with mechanical assistance, to an ash removal system at the other end. In more sophisticated designs this allows the overall combustion process to be separated into its three main activities:
- Initial fuel drying
- Ignition and combustion of volatile constituents
- Burning out of the char.
Grate stokers are well proven and reliable and can tolerate wide variations in fuel quality (i.e. variations in moisture content and particle size) as well as fuels with high ash content. They are also controllable and efficient.
Fluidized Bed Boilers
The basis for a fluidized bed combustion system is a bed of an inert mineral such as sand or limestone through which air is blown from below. The air is pumped through the bed in sufficient volume and at a high enough pressure to entrain the small particles of the bed material so that they behave much like a fluid.
The combustion chamber of a fluidized bed power plant is shaped so that above a certain height the air velocity drops below that necessary to entrain the particles. This helps retain the bulk of the entrained bed material towards the bottom of the chamber. Once the bed becomes hot, combustible material introduced into it will burn, generating heat as in a more conventional furnace. The proportion of combustible material such as biomass within the bed is normally only around 5%. The primary driving force for development of fluidized bed combustion is reduced SO2 and NOx emissions from coal combustion.
Bubbling fluidized bed (BFB) combustors are of interest for plants with a nominal boiler capacity greater than 10 MWth. Circulating fluidized bed (CFB) combustors are more suitable for plants larger than 30 MWth. The minimum plant size below which CFB and BFB technologies are not economically competitive is considered to be around 5-10 MWe.
Pingback: Thermal Processing of Agricultural Wastes
Pingback: Biomass Conveyors: An Overview
Pingback: Rice Straw As Bioenergy Resource
Pingback: Pathways for Waste-to-Energy Conversion | Cleantech Solutions
Pingback: Overview of Biomass CHP | Cleantech Solutions
Pingback: Insights into Biomass Pyrolysis | Cleantech Solutions
Pingback: Cofiring of Biomass
Pingback: Use of Palm Kernel Shells in Circulating Fluidized Bed Power Plants
Pingback: Hotels: Future-proofing the Bottom Line Through Biomass Boilers | Cleantech Solutions
Pingback: Utilization of Date Palm Biomass | BioEnergy Consult
Pingback: Thermal Conversion of Biomass | BioEnergy Consult
Pingback: Overview of Biomass Energy Technologies | BioEnergy Consult
Pingback: Know About Popular Waste to Energy Conversion Routes